The client had 2 existing FG Wilson diesel generators 1500KVA, which we adapted to suit the clients requirements. After every power cut event, the MP1 DC had taken approx. 7 hours to reset the warehouse automation systems, which resulted on a loss of sales on the internet, which MP1 is the flagship site for John Lewis and Partners. Regency was appointed as the principal contractor on site and designed and developed a new generator set control system (COMAP) and replaced the original Woodward Proact engine control system with the Hienzmann Pandoros engine control system, designed the new mains/ generator G99 Synchronising panel (COMAP) onto 2 separate LV switch panels complete with new dual hot/standby Siemens PLC load controls. This has lead to a complete removal of the second outage and allowed the business to continue unhindered, saving 7 hours of valuable trading times.
Regency will go on to provide service support and maintain this site and others for this customer.